What is the in-bond code
The National Electrical Code (NEC) covers grounding and bonding in several articles, but the primary coverage is in Article 250. Typical commercial electrical systems are grounded systems.
Within the system, some things are grounded ... some things are bonded. The terms grounding and bonding are used throughout the NEC. Bonding and grounding requirements overlap somewhat, but they all have a common interest - that of preventing electrical shocks and electrical fires.
There is a distinct difference between grounding and bonding. Each serves a different purpose. However, in most cases equipment that is grounded is also bonded by being connected together.
What Does Bonded (Bonding) Mean?
Bonded (bonding) is defined in NEC Article 100 as: Connected to establish electrical continuity and conductivity. See Figure 1 below which shows two metal boxes bonded together with the metal raceway installed between the two boxes.
Bonding Conductor (Jumper)
Bonding conductor or jumper is a reliable conductor to ensure the required electrical conductivity between metal parts required to be electrically connected. This definition was expanded in the NEC to include bonding conductors as these conductors are often 20 ft (6 m) or longer as used in NEC Chapter 8.
Figure 1 shows two metal boxes bonded together by a conductor installed in the raceway. This bonding jumper would be installed if the raceway were nonmetallic.
Bonding jumpers, equipment
Equipment bonding jumper is the connection between two or more portions of the equipment grounding conductor. A conductor installed in the raceway between the two boxes in Figure 1 would be classified as an equipment bonding jumper.
Bonding jumper, main
Main bonding jumper is the Connection between the grounded circuit conductor and the equipment grounding conductor at the service. A main bonding jumper is clearly shown in Figures 1 and 3.
Figure 3 below illustrates a main bonding jumper that is installed at the service equipment and a system bonding jumper that is installed for separately derived systems. As can be seen, these bonding jumpers perform identical functions: providing a low-impedance path for ground-fault currents to return to their source.
Bonding jumper, supply side:
Bonding jumper supply-side is a conductor installed on the supply side of a service or within a service equipment enclosure (s), or for a separately derived system, that ensures the required electrical conductivity between metal parts required to be electrically connected. This definition was added to the NEC.
It describes a conductor used to bond metallic parts of services and separately derived systems together on the supply side of an overcurrent device.
Because no overcurrent device is located at this position, sizing of the supply side bonding jumper is selected from NEC Table 250.66. Specific reference is made in NEC 250.30 for separately derived systems and in NEC 250.102 (C) for services.
Bonding of Electrically Conductive Materials and Other Equipment
Normally non-current- carrying electrically conductive materials that are likely to become energized shall be connected together and to the electrical supply source in a manner that establishes an effective ground-fault current path. * NEC 250. (A) (4)
Bonding of Electrical Equipment
Normally non-current-carrying conductive materials enclosing electrical conductors or equipment, or forming part of such equipment, shall be connected together and to the electrical supply source in a manner that establishes an effective ground-fault current path * 250.4 (A) (3 )
NEC 250.4 (A) (3) states that normally non-current-carrying conductive materials enclosing electrical conductors or equipment, or forming part of such equipment, shall be connected together and to the electrical supply source in a manner that establishes an effective ground-fault current path.
This refers to the metal race-ways, metal cables, boxes, panelboards, nipples, transformers, and any other electrical materials and equipment related to the electrical installation.
NEC 250.4 (A) (4) states that normally non-current-carrying electrically conductive materials that are likely to become energized shall be connected together and to the electrical supply source in a manner that establishes an effective ground-fault current path.
This refers to items not directly associated with the electrical system, such as metal frames of buildings, metal gas piping, metal water piping, and similar metallic materials.
An electrician makes sure that all electrical raceways, panelboards, and other electrical equipment are properly grounded and bonded in conformance to the NEC.
The issue of grounding and bonding ductwork and metal siding is another problem. For the most part, these building components become grounded and bonded to the electrical system by chance. These components are installed by other trades.
Ideally, except in special cases where isolation is necessary, bonding of all conductive materials should be the goal.
Grounding Service NEC Code 250.24 (A) (1)
Electrical code expert Mike Holt discusses terminating the grounding electrode conductor and 2011 Code compliance with 250.24 (A) (1).
Grounding vs Bonding
- National Electrical Code (NEC) Eldition 2014
- Electrical Wiring, Commercial by Ray C. Mullin, Phil Simmons
Related EEP's content with sponsored links
- Bcwmh fanfiction when sparks fly trailers
- How to play yahtzee flash game
- See white stars while standing
- Who formulated the law of reflection physics
- What objects are measured in grams
- What is angina lacunaris
- How to refill Canon 745 black cartridge
- Doctor, the unearthly child subtitle srt
- How to Make Beetroot Curry Kerala Style
- Colombia Asia Chera's doctor, the episode
- I got some Phils who poured Paris
- Who does JJ Nissen Bread belong to
- Placing the placement of the subwoofer with side fires
- How to replace moen 7400 cartridge
- What is a faulty cold start valve
- How to pronounce beatrice schenk de regniers
- What is it like to live in Houston TX
- What is a machine head guitar store
- Where is Aquafina water source
- How to get piscine fang mhfu
- Masterdex x what is simple payout value
- Loop repeater article C & S grocery wholesalers
- What is grav3yardgirl name
- You know someone is deeply gifted when